Chapter 22 – Inspecting Sub-Areas & Crawl Spaces
We will continue our inspection with the sub-area and crawl space.
Unless your home was built on a concrete slab it will have a sub-area or crawl space.
I found issues in the crawl space even in the best kept homes. This is probably because most people prefer not to enter this area, even if there is enough room to stand.
Sub-areas can be tight confined spaces with only a few inches of clearance between the soil and floor joists or they can be open expansive spaces several feet high. Whether you choose to inspect this area is your decision.
There are various aspects to be investigated in the crawl space including: the foundation system, proper installation of the insulation, crawl space ventilation, dryer vent ducting, HVAC ducting, water heater bracing, water supply and waste plumbing pipes, electrical items, soil condition and excavation issues.
Access to the crawl space can vary from a trap door hidden under carpet in a bedroom to a full size door at the exterior of the building. Ideally, this access opening will be at least 30″ square.
If you see standing water in the opening of the crawl space, STOP!!
DO NOT ENTER THIS AREA UNTIL YOU KNOW THERE ARE NO ELECTRICAL WIRES LYING IN THE WATER. CONTACT A LICENSED ELECTRICAL CONTRACTOR FOR FURTHER INVESTIGATION.
IF WATER IS THE RESULT OF A SEWER LINE LEAK, YOU MUST NOT ENTER THE AREA. SEWER LINE LEAKS CONTAMINATE THE BREATHING AIR.
If you are able to safely enter the crawl space your inspection will include examining the perimeter of the foundation for cracks or damage. Put on gloves, a mask or respirator, kneepads, elbow pads and goggles or protective eyewear before you enter the crawl space.
Inspect the piers and posts to insure they are making good contact with the beams they are supporting.
The home inspector will be looking for excessive cuts and holes in wood construction components. There could be several reasons why the joists and beams under the building have been cut. One example is when a plumber bores a hole to fit pipes and waste lines. Sometimes an HVAC installer will cut a floor joist rather than reposition a heater floor register.
If you recall the discussion on “span” in an earlier chapter, you received a brief education on wood span issues. The underside of your home is constructed of several components that make up the support system and floor of the building.
Beams and joists are the primary components that cross back and forth under the building to create the floor and tie the exterior walls together. Builders and architects follow specific tables to know what material types and sizes can be used to “span” certain distances and still support the structure above.
Let’s have a look at our span image again. The lower drawing shows excessive stress being placed on the beam. What do you think would happen if I cut holes in the board at those areas indicated by the arrows? The larger the holes, the quicker the board will fail.
Holes: Do not bore holes closer than 2″ from joist edges, nor make them larger than 1/3 the depth of the joist.
Notches: Do not make notches in the middle third of the span where the bending forces are greatest. Notches should be no deeper than 1/6 the depth of the joist. Notches at the end of the joist should be no deeper than 1/4 the depth. Limit the length of notches to 1/3 of the joist’s depth.
Boards with holes or notches exceeding these limits must have additional construction members installed to redistribute the load the board is supposed to support.
No wood component of the foundation, flooring or support system should be in contact with the soil. No wood materials stored in the crawl space should be in contact with the soil.
The insulation material should be properly installed and securely fitted.
Proper installation of the insulation in the crawl space has been a controversial issue from time to time. The most common insulation material used in the crawl space is rolled fiberglass batting with a facing. The facing or material coating is foil, plastic or kraft paper. The facing is also referred to as the vapor barrier. Batting in attics is often unfaced.
On many occasions I observed insulation material in the crawl space where the vapor barrier faced downward toward the soil. I reported the insulation was installed upside down.
That report note often generated phone calls from owners and Realtors informing me their licensed contractor said it was installed properly. I had a conversation with a contractor who told me I was wrong and that I should find another line of work. He told me the vapor barrier was to block the vapor that was being released from the soil. After three or four of these episodes, I decided to get the final word on the issue.
I spent several hours researching this subject. Here is a very condensed version of my findings:
In climates of low humidity, the vapor barrier is always placed toward the heated living space. In walls, the vaporbarrier faces inward toward the room; in attics, downward to the rooms below and in a crawl space, upward toward the rooms above. The warm moisture generated inside a building will naturally migrate to the colder surfaces and exterior walls and floor. The moisture can and does penetrate through floors and walls. The vapor retarder (barrier) essentially prevents the moisture generated inside the building from getting trapped in the insulation material where mold and fungus can grow.
In warm climates with high humidity, the denser moisture laden air will migrate towards the conditioned dryer air inside the building so the vapor barrier is installed away from the conditioned living space. The reason is to prevent moisture from getting trapped in the insulation batting, which will reduce its effectiveness. This also prevents the growth of fungus and mold.
In my region of the country, the vapor barrier installed in crawl spaces faces toward the living space above.
Termite contractors will recommend and install a plastic moisture barrier over the entire floor of a crawl space. This barrier traps moisture coming from the soil. This practice is useful in chronic damp conditions and lowers the potential for mold and mildew.
Open crawl space foundation vents provide a cross flow of air and are essential for maintaining low levels of moisture. The vents should be screened to prevent the entry of vermin and should not be blocked. The foundation vents can also be inspected from the exterior of building.
Another source for moisture is the clothes dryer duct pipe. The dryer ducting should be properly secured to the floor joists, not have any sags, not be damaged or disconnected in any way and terminate at the exterior of the building. Dryer ducts over 20’ require a booster fan to exhaust the moist air.
DISCONNECTED DRYER VENT DUCTING DISCHARGED INTO THE CRAWL SPACE MAY ATTRACT TERMITES.
SAGGING AND DAMAGED DRYER VENT DUCTING MAY CAUSE OVER HEATING AND BECOME A FIRE HAZARD.
Check the HVAC ducting of the central heating and cooling systems. Make sure that all ducting is suspended above the ground, is secured to the floor joists and that all wyes, boots and sheet metal joints are attached and insulated.
Clear soil and flammable materials away from the water heater and furnace. Insure the water heater and furnace are properly braced.
Inspect the plumbing water supply and waste lines for damage, leaks and proper installation. To help identify water leaks, run all the water faucets, toilets and showers in the home before inspecting the plumbing and waste lines. The trick is to look at the ground beneath the pipes for wet spots or mud. This will give you a clue as to the condition of the plumbing joints.
There are charts that instruct building contractors on how often certain pipes should be supported to prevent sagging. For your inspection, if a pipe or waste line looks like it is sagging it needs more support.
Inspect the electrical components. The crawl space often has open splices, missing junction box covers and wires that seem to go nowhere. Use the non-contact voltage tester tool to determine if loose, non-terminated wires are hot and dangerous.
Remove all debris from the crawl space area. Debris is anything made of cellulose material that attracts termites and other pests. Cardboard boxes and wood sitting on the dirt are huge red flags for termite contractors and home inspectors. A way to impress the termite contractor and the home inspector is to rake the soil in the crawl space. Leave the lines made by the rake. This is very cool.
The exterior grade slope and landscape irrigation practices can have a huge impact on the dryness of the crawl space. Record any signs of moisture or any place where water appears to have been flowing.
The home inspector will look for areas of over-excavation of the soil. The foundation, piers and posts and retaining walls require support from the earth in order to support the structure above.
In the mountains where we work and live, many homes were built on a hillside. These buildings often had expansive areas underneath. We found homeowners who had altered this sub area for storage. In order to have a nice flat floor they would remove or “excavate” excessive soil around the foundation, stem walls and support posts.
Another common practice was partially enclosing the sub area for additional living space. This presents problems such as: floor joists and wall components in contact with the soil; inaccessible crawl space under the new room; compromised ventilation of the sub area and excessive excavation of the soil.
It was unknown if these rooms were constructed under permit but the biggest issue was the installation of access stairs from the floor above. I am not sure how a person can think it is ok to cut out several floor joists for a stairway and not properly support the floor.
Such practices compromise the foundation of the building and will always generate a note in a home inspection report. The note will recommend that a licensed Structural Engineer be called to evaluate the changes. Nothing will raise the hair on the back of a Realtor’s neck faster than calling for an engineer’s evaluation. The need for such an evaluation usually indicates a serious problem, and such problems may jeopardize a smooth close.
SUB AREAS AND CRAWL SPACE FINDINGS: REMEDIES AND SOLUTIONS
Broken, damaged or deteriorated framing members should be inspected and repaired by a licensed contractor.
Hairline cracks in the stem walls of the foundation are not uncommon. Unless they are shearing (twisting in different directions) or are large enough to fit a nickel in the crack, concern should be minimal. A licensed Structural Engineer would need to provide additional information.
Insulation that has been damaged or is hanging down should be secured or replaced. Open up blocked foundation vents and repair or replace damaged foundation vent screens.
Secure or repair damaged or detached heating and dryer vent ducting.
Brace the water heater. Clear away soil from the water heater and furnace housing. In California, it is state law that the homeowner must brace the water heater before the close of escrow. Check with a local plumbing company or your municipal building department to learn the necessary requirements for your region.
Hire a qualified tradesman to repair water leaks and electrical issues. Splices should be in junction boxes and open junction boxes should be covered.
Dampness in the crawl space soil may be a seasonal condition. In some areas, naturally occurring moisture in the ground is normal. Plastic sheeting set on the crawl space floor is a common way to trap and retard condensation issues and reduces the potential for organic growth.
The source of muddy, standing or running water should be thoroughly investigated. Excessive water intrusion can be detrimental to the integrity of the foundation. It can also cause deterioration in the wood underpinning. If it is determined that the water is coming from an underground source and is more than seasonal, a sump pump or “French” drain may be a necessary. Contact a Geotechnical Engineer to determine how best to address this issue.
Excessive excavation issues can usually be resolved be supporting the soil with retaining walls. Questionable construction practices can be looked at and repaired without necessarily calling in a Structural Engineer. A good contractor can determine a reasonable course of action for repairs. Let the contractor call an engineer if needed.
An additional 86 images with descriptive captions are available in the 27 Dollar Home Inspections eBook.
Click here to move on to
Chapter 23 – Inspecting Pools, Spas, Alarm Systems, Telephone Service. etc.
Tagged with: "crawl space standing water" slope hill side • "crawl space" dimensions california code • "door to crawl space" • "excavate a crawl space" • "foundation vent screen" • "junction box" crawl space vapor barrier • "plastic vapor barrier" cover moist subarea • "should a crawl space be inspected" • "trap door" "crawl space" • +hillside house crawl space standing water • 23" batting 22" space insulation how to • access electrical "junction box" "crawl space" • are electrical junctions in crawl space legal • are junction boxes legal in crawl space under house in california • bathroom over inaccessible crawl space • bathtub subarea • bathtub supports on a crawl space • bedroom/crawspace/secret entrance • bedrooms over crawl space dangers • being safe in tight crawl spaces • best crawl space junction box • best fix for dryer vent damage to joists • best location crawlspace floor trapdoor • best place to install trap door to crawspace • best way to insulate trap door to crawl space • best wood for crawl space door • blocked crawl spaces • blocked foundation vent • blocked sewer line escrow california • blocking vents-passing inspection • bowed sewer pipe in crawl space • boxes in the crawlspace • boxes on plastic in crawl space caused mold in dirt • bracing a sagging floor w a dirt floor crawl space • bracing crawlspace trapdoor • bracing floor for a crawl space access • broken beam in inaccessible crawl space • build a post to support crawlspace beam • build a support beam for crawl space pictures • build trap door crawl space • build trap door under carpet • build under house crawl hole • building inspections of crawl spaces • building inspector found a broken support beam in the crawl space • By California law must there be a crawlspace under the kitchen • CA building code exclusion on subarea ventilation • ca building code for subarea vents • calculate area of foundation venting california • california • california building a crawl space • california building code for subarea beam replacement • california building code install insulation in a sub area • california code crawl space clearance • california code for a junction box in basement crawlspace • california code for crawl space access dimensions • california code size for under house crawl space • california crawl space insulation • california crawl space tub drain pipe plastic • california crawlspace law? • california house crawl space water pipes pictures • california insulation inspection checklist • california law homes crawl spaces furnaces problems • california regulations water heaters crawl spaces • california sub area access • california water pipe crawl space code • can a rake or shovel attract termites if stored in the crawl space • can a water heater be installed in a pit in the ground crawl • can a wet crawl space cause a house to fail inspection • can crawl space entry be blocked by plumbing pipes • can crawlspaces be made deeper • can dryer vent line be attached to floor joistsinstallation • can furnace be installed in the crawl space california • can having water in crawl space pass inspection • can i box in plumbing in crawl space • can i cover up mould over dirt under house with plastic barrier • can i cut a floor joist underneath a door • can i put a junction box in the crawl space under the house • can insulation be installed upside down in crawlspace of house? • can insulation be upside down crawl space • can insulation installed backwards cause mold in a crawl space • can junction boxes be underneath a pier and beam home in the crawl space • can lumber be stored in crawl space under house • can my clothes dryer condensation attract termites? • can wood be used as support post in crawl space • can you fail a home inspection because a damp crawl space • can you install a furnace in a crawl space in california • can you make a hole in the beam of the house for water pipes with california code • can you put junction box in crawl space • carpet covered crawl space door • carpet for crawl space door • carpet installation over crawl space hatch • carpet over crowl space entrance • carpeting a room over crawl space • carpets over a crawl space • clearance from earth to j-box in a crawl space • concerns with inslation upside down in crawlspace • confined space home inspector crawl space • could disconnected dryer vent cause mold in crawl space • cracked soil in sub area • crawl space "trap door" dimensions • crawl space access door illustrations • crawl space access door in contact with ground • crawl space access door insulated • crawl space access door location • crawl space access doors size california • crawl space access size ca • crawl space and plastic j boxes • crawl space beam failed inspection • crawl space beam splice support • crawl space beams sagging causes • crawl space brace • crawl space brace or sheeting • crawl space dimensions california • crawl space dryer vent pool water • crawl space electrical items • crawl space entrance under carpeting • crawl space excavation california • crawl space exterior vent clearance • crawl space foundation pictures • crawl space grates with dryer vent hole • crawl space heaters inspection tips • crawl space hole water heater • crawl space hvac register • crawl space inaccessible • crawl space insulation hang loose • crawl space insulation installed upside down • crawl space insulation installed upside down impact on home • crawl space insulation installed upside down oregon • crawl space insulation paper backed fiberglass insulation moisture subfloor bowed • crawl space insulation upside down • crawl space insulation upside down installation • crawl space joists sit directly on soil • crawl space junction box hanging • crawl space law california • crawl space moisture problem insulation upside down • crawl space post and pier pads photos • crawl space support beam repair kit • crawl space support column distance california code • crawl space trap door flooring • crawl space trap floor access doors • crawl space vapor barrier installation under furnace • crawl space venting requirements in pa • crawl space water leak. replace plastic? • crawl space wood support systems • crawl spaces beams that have been cut problems • crawl spaces telephone line installation • crawlspace access size california • crawlspace can vapor barrier go over sewer pipe • crawlspace joist mildew pictures • crawlspace joist size • crawlspace standing pools of household sink waste • crawlspace subarea • Creating inaccessible crawl space under my • crowl space • cut floor joist hvac • cut hole in floor joist for hvac duct • cut hole in floor to get access to crawl space • cut holes in the upside down insulation in my crawl space • cut trapdoor foundation access • cutting a hole in the floor for crawlspace access • cutting access for crawl space • cutting additional crawl space vent holes • cutting carpet in crawl space • cutting floor joists for hvac • cutting floor to access crawlspace • cutting hole for crawlspace • cutting hole in foundation wall for crawl space access • cutting joists for for furnace venting • cutting the foundation to access crawl area • damage or disconnected vents • damp carpet in bedroom with crawl space • damp soil in hillside crawl space • damp soil in subarea house • dampness in subarea • dangerous? • detached dryer vent • diagrams of dryer vent installation in wall to crawl space • dirt crawl space under kitchen • dirt crawl space water heater installation • distance between a beam and soil in a crawlspace • distance between crawl space vents • distance from dirt to floor joists in crawl space • distance from main cut off from crawl hole door • diy crawlspace insulate inaccessible • do all floor joist need support post for stem walls • do i have to remove floor insulation for the inspector to inspect under house • do you have to brace insulation in crawl spaces? • do you need a vapor barrier to pass inspection • does a homeowner have to fix defective items on a home inspection report in tennessee • does crawl space insulation attract termites • does damp crawl spaces attract termites • does moisture under plastic in crawl space cause a failed inspection? • does there have to be plastic under a house to pass inspection • door down to crawl space • dryer duct floor joists • dryer duct installation clearance joists • dryer lint hanging off pipes in crawl space • dryer pipe floor joist cut • dryer vent broke in crawl space • dryer vent broke under crawl space moisture california • dryer vent cap clearance above ground california • dryer vent crawl space ground hang • dryer vent detached • dryer vent discharge under house crawl space • dryer vent in floor to foundation picture • dryer vent running to crawl space pa home code • dryer vent through support beam • dryer vent under crawlspace to exterior • dryer vents for tight spaces • easy way to fix foundation vent screen • elbow guards for crawling instpectors • elbow pads for crawling houses • electric hanging crawl space heater • electrical in sub area • electrical junction box in crawl space • electrical junction box missing cover in crawl space • electrical junction box under house on piers O.K. • electrical wires on the crawl space flooring • electrical wires on the soil in the crawlspace • examples of non-flammable items that can be stored in a crawl space • excavate california crAwlspace • excavating a sub area • excavating crawl space in california • excavating dirt from a crawl space • excavating dirt from home foundation under decking • excavating house sub area • exhaust "vent pipe" installation "redmond oregon" • fixing a sub area access • fixing foundation vent screens • floor insulation crawl space california law • floor joist cut for furnace • floor joist cut to install box under furnace • foundation crawl space bracing • foundation piers at crawl spaces installation floor joist • foundation vent clearance • foundation vent ground clearance • foundation vent moist reading at 12% • foundation vent retain walls • foundation vents installed upside down • fungal growth on floor joist proper repair • furnace in crawl space through trap door • get insulation out of inaccessible crawl space • getting the mold out of subarea • getting to pipes in an inaccessible crawlspace • ground clearance crawl space california • ground clearance for central heating • ground clearance joist expansive soil • growths on floor joists • hairline crack stem wall • HAIRLINE CRACKS IN CRAWL SPACE MOISTURE FLOOR JOIST • hairline cracks in stemwall • hanging crawl space insulation upside down • hanging pipes in crawlspace • heater in crawl space laws • hidden crawl space access • hidden trap doors in floor insulation • hide crawl space access door • hole in foundation in crawl space • hole to crawl space under dryer • home inpector elbow pads • home inspection checklist wooden • home inspection crawl space insulation • home inspection crawl space joists • home inspection crawlspace moisture writeup • home inspection excess soil underneath any support issue? • home inspection found water line in crawl space • home inspection of foundation crawl space • home inspector access at crawl space • home inspector elbow pads • home sewer system california crawlspace • home support beams in crawl space loose • home with crawl space hole to enter • house crawl space loose boards • house floor joists are in contact with dirt • house inaccessible hidden crawl space" • house sub area • house sub area venting • house subarea • HOW CAN I INSULATE A TIGHT CRAWL SPACE • how do i insulate an inaccessable area • how do I know if I my house have holes • how do I know if I my house have holes, damage or disconnected vents • how do i know if my wood floor joists are vented properly • how do i notch a floor joist to install a dryer vent • how do you install piers in crawl area • how do you insulate a floor that was built on a pads. The space between the floor joist and the ground is about 20 inches and open for ventilation." • how many vents are required in a sub area in california • how many vents should the sub area have • how often do you have to go in crawl spaces as a plumber • how often do you see water in crawlspace home inspection • how often replace pipes in crawl space • how often replace plastic vapor barrier crawl space • how often should a crawl space be inspected • how often should you have crawl space inspection • how to access a crawl space that is unaccessible tp look inside • how to access crawl spaces under kitchen • how to access the crawlspace under the kitchen? • how to calculate vents for subarea of a house • how to carpet an access hole to crawl space • how to carpet crawl space door • How to crawl under a house without getting dirty • how to cut a trap door to a crawl space • how to cut carpet for crawl space entrance • how to cut crawl sapce access door in floor between joists • How to cut the fundation for crawling space • how to determine best place for crawl space door in floor • how to excavate a crawl space to put in hvac system • how to fix a water pipe in a tight crawl space • how to fix sagging floors with an inaccesable crawl space • how to fix screen for crawlspace vent • how to hang dryer vent between floor joists • how to have crawl space pass inspection • how to insalate a crawl space trap door? • how to inspect a craw • how to inspect a crawl space • how to inspect a house foundation crawl space • how to inspect crawl beams • how to inspect Crawl Space • how to inspect floor joists • how to install a trapdoor in the floor • how to install carpet on crawl space hatch door • how to install extra floor bracing in crawl space • how to install insulation batting face down or up in crawl space • how to install subarea access cover • how to insulate a wood plank floor above dirt crawl space • how to insulate an inaccessible crawl space • how to insulate dryer vent pipe crawl space • how to insulate under floor with inaccessable crawl space • how to investigate crawl space water leak • how to know if my wood foundation in crawl space is OK • how to make access in an inaccessible crawl space • how to make crawl space vent holes • how to pass a water pipe under a foundation into the crawl space • how to pass crawlspace inspectio • how to pass insulation inspection • how to properly cut a floor joist for access • how to properly inspect crawl space for insulation • how to put vapor barrier in subarea • how to rectify insulation in crawlspace being upside down • how to repair electrical in a crawlspace • how to replace plastic foundation vents • how to replace wire in exterior foundation vents • how to thoroughly inspect a crawl space • how+to+cut+a+sub+area+access at your home • howto stop a underground water leak in crawl space • http://www.27dollarhomeinspections.com/chapter-22--inspecting-sub-areas-crawl-spaces/ • hvac cut floor joists • HVAC ducting clearances in crawl space California • hvac ducts sagging in crawl space • hvac install cut floor joist • hvac installers cut my floor joist • i can fit a nickle in a crack of a foundation • identifying plumbing lines in crawl space • images of fungus found in crawlspaces • images of water leaks in crawl space • inaccessable space excavation • inaccessible crawl space • inaccessible crawl space access inspection • inaccessible crawl space cut drywall • inaccessible crawl space insulation • inaccessible crawl space moisture barrier • inaccessible crawl space oregon • inaccessible crawl space problems • inaccessible crawl space vapor barrier • inaccessible crawlspace plumbing • inspecting a craw • inspecting a crawlspace • inspecting a tight crawl space • inspecting an inaccessible crawlspace • inspecting crawl space • inspecting for termites in dirt crawl space • inspecting inaccessible crawl spaces • inspecting joist cut for hvac • inspecting my crawl space • inspecting support beams in crawl • inspecting tight crawl space • inspecting under house with tight crawl space • inspection reports on crawlspaces • inspection trap door • inspector inaccessible crawlspace • install insulation crawl space upside down • install insulation in crawlspace under pier and p • install plastic to floor joist in crawl space • install support posts in crawl space • installation crawl space trap door video • installation of hvac in crawl space hanging • installing a trap door into crawl space • installing a water heater in a dirt crawlsspace • installing batting insulation in damp crawl space pictures • installing dryer vent booster under the floor joist • installing dryer vent through floor joist • Installing fiberglass batting in a crawl space • installing hidden trap door to crawl space • installing insulation in subarea • installing+a+wood+floor+in+my+crawl+space • insulate area inaccessable crawl space • insulate furnace junction box in crawl space • insulate inaccessible crawl space • insulating an inaccessible crawl space • insulating an inaccessible crawlspace • insulating floor over inaccesable crawl space • insulating inaccessible crawl space • insulating inaccessible crawl spaces • insulating inaccessible space • insulating trap-door to crawlspace • insulating+dryer+vent+opening+in+an+enclosed+space • insulation hanging down in inacessible crawl • insulation in crawl space loose and hanging • insulation installed backwards crawl space • insulation installed upside down • insulation subarea california • insulation upside down in crawl space • is a liner required in a crawlspace to pass home inspection? • is dryer vent safe in crawl space • is it legal to pass a home inspection without insulation in the crawl space in pa • is it ok to cut i beam in crawl space • is it ok to have a junction box in crawl space • is it okay to cut access for crawl space • is it okay to vent a sewer line in a crawl space • is it safe to excavate dirt from a tight crawl space? • is it typical to see water in a crawl space in the mountains? • is open dirt in a crawl space legal • is that okay • is there a concern if sewer water leaks from hple in the main elbow going out of the house in a crawlspace • is there any upside to venting the crawlspace • is waste line leak dangerous in home • is wrong way facing insulation causing mildew crawl space • Joist cut for waste line • junction box crawl space damp • junction box crawl space not attached • junction box in crawl space • junction box in crawl space clearance • junction box in crawl space legal • junction boxes crawl spaces • knotched wood incorrectly in a beam in the crawlspace • leaky crawl space pass inspection • low clearance crawl space excavate • main beam clearance from earth in crawlspace • making a hidden entrance in floor for crawlspace • making a trap door to crawl space • making a trap door to crawlspace • mask to inspect crawl space • min crawl hole size ca • minimum crawl hole in ca • minimum crawl space access • minimum dimensions for foundation crawl space california • minimum space between dirt crawl and floor joist • minimum space between floor joist and ground • moisture "inaccessible crawlspaces" inspecting • Moisture barrier Home inspection writeup • mold from detached dryer vents • move crawl space opening • muddy soil in the sub floor area • musty odor coming from inaccessible crawl space • my builder has installed floor joists 22 inches is that safe • my dryer causes moisture in crawl space • my house failed inspection because of the crawl space • neck brace crawl space • need to insulate dirt crawl space under kitchen • not enough clearance between ground and floor joists in crawl space • nothing to attach junction box to crawl space • onspanin • open p trap in crawl space • open pipe coming out of ground in crawl space • open splice allowed in crawlspace • organic growth in crawl space • organic growth/ fungus in the crawl space joists • organic growths on floor joists in crawl space • passing crawlspace inspections • photo proper crawlspace entrance • photos of fungus in crawl space • pics of installed furnace in a crawl area • picture of crawl space screens • pictures from installing water lines in crawl space • pictures of crawl foundation construction • pictures of crawl space foundation utility • pictures of crawl space openings • pictures of damp crawl spaces • pictures of damp crawl spaces homes • pictures of foundation ventilation • pictures of insulation floors with crawl space • pictures waste line of shower in crawl area • pier and beam insulation under houses California • pipes sagging under building foundation • piping support in crawl space • pitchers of crawlspaces • plastic over soil in craw space • plastic sheeting as moisture in subarea • plastic shetting crawl space vent holes • plumber is notching beams to install drain pipe • plumber+holes+cut+into+main+support+beam+of+the+house • plumbing pipes in inaccessible space • problem caused by insulation under crawl space is upside down • Problems caused by discharging dryet air in crawlspace • problems with carpets from dirt crawlspace • problems with inspecting crawl spaces • proper hvac duct installation in crawl space • proper installation of sewer line in crawl space • proper way to install batting in crawl space • proper ways to hang electrical wires crawl space • raising crawl space floor above wood support posts? • rake subarea termites • redmond • redmond, wa "crawl space vapor barrier" municipal code • remove spaces using inspect • removing floors foundation crawl space wood post • repair hvac cut floor joists • repairing house foundation vent screen • replace crawl space joist • replace foundation vents how often? • replace house supports dirt crawl • replacing h vac cut joists foundation crawl space • replacing wooden support in Crawl Spaces • required distance between beams and soil in crawl spaces • retaining walls in crawl space • rule of thumb for hole in joist • run shower p trap in crawl space • run water pipe Foundation vent screens • running central heating pipe in crawl space • safe to crawl sub area • sewer access junction under my kitchen floor • sewer line leaks in crawl space • sewer pipe suport in crawlspace • sewer waste on a dirt crawling space • shifting soil in crawl space • should a mosture barrier in crawl space be placed under furnace • should I install plastic sheeting crawl space california • should i vent dryer into sub area • should pipes be hung off the floor in a crawlspace • should plumbing lines be supported in crawl space • should you be able to fit a nickel in the crack of a foundation • should you cut holes in the platic mosture barrier on the dirt in the crawl space • show me pictures of dryer venting in a crawl space sub floor • size of crawl hole vent • size of crawl space access California • small crawl space under kitchen floor is inaccessible • soil line above foundation cause mold california • soil to wood contact crawlspace • some inaccessible crawl space, do i have to fix • span problems in crawl space • standing water crawl space building code washington state • standing water crawl space wire • standing water in crawl space not necessarily mold • state of california what statute requires insulation of subareas • stem walk crawl space california • steps to pass inspection of conditioned air installation • sub area access cover • sub area access wall • sub area damp home inspection • sub area home inspection • sub area house • Sub area mold • Sub area mold on dirt • sub area of home • sub area of house • sub area ventalation • sub areas of a home • sub foundations hvac ducts • sub-area access doors • sub-area door • sub-area ventilation • subarea access picture • subarea beneath vent screen • subarea clearance from soil to joist and subfloor • subarea earth dampness property inspection • subarea earth was damp at inspection • subarea foundation crack • subarea house • subarea insulation installed upside down • subarea is wet and inaccessible problem • subarea joist • subarea of home moist • subarea of house • subarea support posts • subarea vents in house • subwoofer in floor register joist house • support beam cut crawl space • support beam in crawl space has opening for drain pipe for bathtub • support electrical wires in crawl space • support foundation vents • support posts go into dirt in crawl space • support under furnace in crawl space • supporting a furnace in a crawl space • telephone lines hanging down in crawl space • The rule about inspecting crawl spaces • the rule about inspectong crawl spaces • they crawl sub • tight crawl space • tight crawl space excavation • tight crawl space for water pipe repair • tight crawl space inspecting • tools to "excavate dirt" from crawl space • trap door floor crawl space • trap door floor joists installation • trap door inside house to access crawl space • trap door to crawl space • unaccessible crawl space • under floor sub area vapor barrier • under what section is subarea ventilation • using insulation upside down crawl space • vapor barrier for plank flooring over dirt crawl space • vapor barrier in inaccessible crawl space • vapor barrier over soil crawl space california building code • vapor barrier upside down in crawl space insulation • vent holes in crawl space covered by boards • vent holes on house sub area • vent screens crawl space hole • wa "crawl space vapor barrier" municipal code • washington state code bracing water heater • washington state fire code vented crawl space insulation • waste pipe crawl space entrance • water appears hole in crawl space • water heater installation in crawl space california • water heater on soil crawlspace • water in a dirt crawl hole • water in crawl space opening photos • water in crawl space under furnace problems • water in inaccessable crawl space • water in subarea of a house • water in underground ducting hvac • water seeping up into crawl space Redmond, Oregon • water subarea inspection • water supply line crawl space through joists • water supply line leak crawl space califrornia • water supply lines in unaccessible crawl space • water under carpet above crawl space • wet crawlspace with bowing beams • what are subareas of the home • what causes insulation to hang down in a crawl space • what causes water in crawl space in washington state • what does a home inspector look for in a crawl space • What does moisture level in crawl space have to be to pass inspection? • what happens if duct pipe sags? • what happens if i cut a floor joist • what if vapor retarder is upside down in crawl space • what is a subarea in property • what is a subarea of a house • what is california code for a sub area access clearance? • what is sub-area in a house • what is subarea of house • what is subarea space • what is the best way to do repairs to a pier and beam floor can you splice joycs • what is the minimum requirement for a crawl space access to a subarea • what is the minimum size of a sub-area access hole • what is the plastic pipe in floor of crawl space • what is the requirment for vents in subarea • what is the size of an inspection crawling space • what is the sub area of a house • what is the subarea of a house • what must moisture level in crawlspace be to pass inspection • what size vent holes for crawl • WHAT TO DO WITH subarea growing mold • what to look for when inspecting foundation/crawl space • whats ca code for min crwal space • when underfloor insulation is installed upside down • where is the facing on insulation batting • where should hardwood to tile transition be in doorway • why does my house have a supporting beam in crawlspace • why would someone use wooden supports in a crawl space • will a crawl space access cover in the bedroom pass inspection • will a cut floor joist always fail • will a damp crawl fail a home inspection • will a damp crawl space fail home inspection • will a damp crawl space fail inspection • will a damp crawl space pass inspection • will a dryer vented into a crawlspace pass inspection • will a house pass inspection if there is water under the moisture barrier • will a wet crawl space pass inspection? • will a wet crawlspace pass inspection • will an inaccessible crawl space pass inspection • will crawl space with water standing pass inspection? • will dampness in a crawl space cause a home inspection failure • will dampness in crawl space fail home inspection? • will home inspection fail with mold in crawl space • will home inspector inspect crawlspace • will house fail inspection if there is no vapor barrier in crawl space? • will inspector's move insulation in crawl space • will inspectors look for a vapor barrier in my crawl space • will sandwiching crawl space beams pass inspection • Will water in a crawl space fail an inspection • Within What Distance Is A Main Cutoff Located To The Crawl Hole Door • wood box in crawl space • wood joists over dirt living area • wood soil contact at the subarea of crawlspace • wood support in crawlspace inspection how to • wood supports crawl space home inspection • wood supports under crawl space • WOOD TO DIRT CRAWL SPACE DISTANCE • wood to soil contact in crawl space • would a damp crawspace fail a home inspection
Like this post? Subscribe to my RSS feed and get loads more!